How Do You Inspect A Portable Eyewash Station?
By regularly inspecting your portable eyewash station, you can help ensure it remains functional and safe for use in emergencies.
- Check the exterior: Examine the overall condition of the eyewash station, looking for any signs of damage, leaks, or corrosion. Ensure it is easily accessible and visible, with proper signage and clear instructions for use.
- Inspect the water: Ensure the eyewash water is clean, clear, and free of contaminants. Check the expiration date, and replace the water if it's expired or contaminated.
- Test the operation: Activate the eyewash station by pressing the release mechanism or lever. Observe the water flow; it should be steady and strong, with both eyewash nozzles functioning properly. The water should be tepid, not too hot or cold.
- Inspect the nozzles: Check the eyewash nozzles for cleanliness and proper function. The nozzles should be covered when not in use to prevent contamination. Clean the nozzles if necessary.
- Examine the drain: Inspect the drainage system, if applicable, to ensure it's free of debris and draining correctly.
- Check the pressure: For pressurized units, confirm that the pressure gauge is within the recommended range specified by the manufacturer.
- Record the inspection: Document your findings, including the date, any issues encountered, and actions taken to resolve them. Keep a log of inspections for future reference.
- Perform routine maintenance: Follow the manufacturer's recommendations for maintenance, including cleaning, refilling, and replacing parts as needed.