Application: Electric heat-traced stations prevent freezing even in extreme conditions. Thermostat regulated units are heated by self-limiting heat-tracing cable wrapped around internal pipe. Units are intended for cold weather use down to -40Â¬âˆžF. See â€šÃ„Ã²Tempering Valvesâ€šÃ„Ã´ section to ensure tepid water compliance with ANSI Z358.1-2014.
Heating Cable: Self-regulated with external termination guards. Thermostat activates when internal piping temperature falls below 75Â¬âˆžF. FM, UL, and CSA approved for Class I, Division 2, Groups B, C, and D.
Electrical System: Unit is fully wired at factory. Junction box and components rated for Class I, Division 2, Groups B, C, and D. Requires 120 VAC single phase power supply.
Jacket/Insulation: UV-resistant orange ABS plastic with polyethylene foam insulation. Jacket sections secured with removable stainless steel screws for easy maintenance.
Shower Head: 10" diameter stainless steel with 20 GPM flow control.
Shower Valve: 1" IPS chrome-plated brass stay-open ball valve. US-made with brass ball and TeflonÂ¬Ã† seals. Includes stainless steel actuating arm and 29" stainless steel pull rod.
Spray Head Assembly: Freeze-resistant with float-off dust covers and internal flow contro
Eyewash Valve: 1/2" IPS chrome-plated brass three-way self-draining stay-open ball valve. US-made with brass ball and TeflonÂ¬Ã† seals. Includes 1/2" NPT port to drain water from spray heads after use.
Pipe and Fittings: Schedule 40 Type 304 stainless steel.
Supply: 1-1/4" NPT female top inlet.
Sign: ANSI-compliant identification sign.
Quality Assurance: Factory tested prior to shipment. Ships fully assembled and crated. br>
|Eyewash Bowl Material||No Bowl|
|Item||Combination Safety Shower Eyewash Stations|
|Shower Head Material||Stainless Steel|
|Shower Operation||Pull Down Arm|
WARNING: California Residents
This product and/or packaging can expose you to chemicals including Styrene, which is known to the State of California to cause cancer and birth defects or other reproductive harm. For more information go to www.P65Warnings.ca.gov.