Availability : Usually Ships in 10-12 Business Days
APPLICATION: Single pole, double throw flow switch for use with emergency equipment. Flow switch is installed in water supply line upstream of emergency unit. When unit is activated, switch senses the movement of water in the supply line. Switch can be used to activate alarm horn and light, and sends electrical signal to monitoring system.
INSTALLATION: Flow switch is mounted in tee fitting that is installed in water supply line to emergency unit. Switch must be installed with tee fitting in horizontal position, flow switch body in vertical position and at least 6" from closest fitting. Direction of flow is marked on switch body. Furnished with weatherproof electrical junction box with gasketed cover. Switch requires 5 amp, 125 volt electrical connection.
ACTIVATION: AP275-615 activates at 2.4 GPM, deactivates at 2.0 GPM. AP280-615 activates at 3.0 GPM and deactivates at 1.75 GPM. AP285-615 activates at 2.4 GPM and deactivates at 2.0 GPM.
QUALITY ASSURANCE: Unit is factory tested prior to shipment. br>
WARNING: California Residents
This product and/or packaging can expose you to chemicals including Styrene, which is known to the State of California to cause cancer and birth defects or other reproductive harm. For more information go to www.P65Warnings.ca.gov.